U.S. Navy Settles Underground Storage Tank Violations at Hampton Roads Facility
Release Date: 04/26/2012
Contact Information: Donna Heron 215-814-5113 / email@example.com
PHILADELPHIA (April 26, 2012) -- The U.S. Navy has agreed to pay a $5,855 penalty to settle alleged underground storage tank (UST) violations at its Building NH94, located at 7918 Blandy St., Norfolk, Va., the U.S. Environmental Protection Agency announced today.
There are three 25,000-gallon underground storage tanks at this facility containing diesel fuel. Each UST is required to be tested every three years to make sure the tank is not corroded and that the corrosion protection system is operating properly. During a March 2011 inspection, the inspectors found that these tanks had not been tested since 2004.
The $5,855 settlement penalty reflects cooperation of the U.S. Navy with EPA in the investigation and resolution of this matter. The Navy has certified its compliance with applicable UST requirements and the tanks were tested for corrosion on April 4, 2011.
Underground storage tanks must be tested to prevent leaks, because the greatest potential threat from a leaking UST is contamination of groundwater, the source of drinking water for nearly half of all Americans. These leaks can threaten public safety and health as well as the environment because UST systems contain hazardous and toxic chemicals. Cleaning up petroleum leaks is difficult and usually expensive. Federal regulations ensure that USTs are structurally sound because it is easier and less costly to prevent leaks before they happen.
For more information on underground storage tanks, go to: http://www.epa.gov/oust/index.htm.