Rule Title: Monitoring systems: Performance evaluations
|Nevada Administrative Code|
|Nac, Chapter 445B, Chapter 445, Air Controls – General Provisions|
Final Federal Register Date
Federal Register Citation #
|72 FR 19801|
Nac, Chapter 445B, Chapter 445, Air Controls – General Provisions (doc, 58 KB)
NAC 445B.259 [445.686] Monitoring systems: Performance evaluations.
1. During any performance tests required under NAC 445B.252 or within 30 days thereafter and at such other times as may be required by the director under § 114 of the Act, the owner or operator of any affected facility shall conduct continuous evaluations of the performance of monitoring systems and furnish the director within 60 days thereof two or upon request more copies of a written report of the results of such tests. These evaluations must be conducted in accordance with the specifications and procedures provided in this section and NAC 445B.260.
2. Except as provided in NAC 445B.260, continuous monitoring systems listed within this subsection must be evaluated in accordance with the requirements and procedures contained in the applicable performance specification of Appendix B of 40 C.F.R. § 60. Continuous monitoring systems for measuring:
(a) Opacity of emissions must comply with Performance Specification 1.
(b) Nitrogen oxide emissions must comply with Performance Specification 2.
(c) Sulfur dioxide emissions must comply with Performance Specification 2.
(d) The oxygen content of carbon dioxide content of effluent gases must comply with Performance Specification 3.
[Environmental Comm’n, Air Quality Reg. §§ 2.17.3 & 188.8.131.52, eff. 12-4-76]—(Substituted in revision for NAC 445.686)
This SIP Citation Was Last Modified on January 29, 2013. EPA has attempted to assure that the action logs accurately reflect the actions published in the Federal Register. If there are discrepancies, however, the Federal Register is the official record. Send State Implementation Plan comments and questions to firstname.lastname@example.org.